Pipe Specification A A NPS 1/2 — 10″ Schedule 10 and Schedule 40 Grade A or B for type E or S pipe, wall thickness schedule ASTM A, the. The ASTM A is the standard for black and hot-dipped zinc-coated (galvanized ), welded and seamless steel pipes designed for fire protection. Contact us!. ASTM A / ASME SA STANDARD SPECIFICATION FOR BLACK AND HOT-DIPPED ZINC COATED(GALVANIZED) WELDED AND SEAMLESS STEEL .
|Published (Last):||12 January 2015|
|PDF File Size:||4.63 Mb|
|ePub File Size:||14.30 Mb|
|Price:||Free* [*Free Regsitration Required]|
ASTM A795 ERW STEEL PIPE
Pipe ordered under this specification is intended for use in fire protection systems. Note 2 — Successful bending of pipe is a function of equipment and technique as well as pipe properties.
Within the text, the SI units are shown in brackets.
Pipe having other wall thicknesses may be furnished provided such pipe complies with all other requirements of this specification and the outside diameter is as given in Table 2. The steel shall conform asstm the required chemical composition. Referenced Documents purchase separately The documents listed below are referenced within the subject standard but are not provided as part of the standard.
Each length of pipe shall be subjected to a hydrostatic test without leakage through the pipe wall. See Table 2 for dimensions.
Combining values from the two systems may result in non-conformance with the standard. It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use.
This abstract is a brief summary of the referenced standard. ASTM does not give any warranty express or implied or make any representation that the contents of this abstract are accurate, complete or up to date. Finally, flattening test shall be performed on the pipe zstm accordance with, electric-resistance-welded pipe, and furnace-welded pipe.
The pipe may be bent, but it is not intended for bending made at ambient temperature wherein the inside diameter of the bend is less than twelve times the outside diameter of the pipe being asrm Note 2. Historical Version s – view previous versions of standard. Link to Active This link will always route to the current Active version of the standard. As an alternative to the hydrostatic test, and when accepted by the purchaser, each pipe shall be tested with a non-destructive electrical method.
The values stated in each system may not be exact equivalents; therefore, each 7a95 shall be used independently of the other.
Steel Pipe ASTM A
It is informational only and not an official part of the standard; the full text of the standard itself must be referred to for its use and application. This standard does not purport adtm address all of the safety concerns, if any, associated with its use.
The pipe may be bent, but it is not intended for bending made at ambient temperature wherein the inside diameter of the bend is less than twelve times the outside diameter of the pipe being bent.
See Table 1 for dimensions. This specification covers black and hot-dipped zinc-coated galvanized welded and seamless steel pipe for fire protection use.